74:53:01:26. Requirements for holding tanks. The requirements for holding tanks are as follows:
(1) The minimum liquid holding capacity shall be 1,000 gallons or the wastewater flow generated over a period of 7 days, whichever is greater. There shall be no discharge of effluent from the tank;
(2) The tank shall be equipped with a high-water alarm positioned to allow at least 3 days of storage after the alarm is activated;
(3) Holding tanks shall conform to the requirements for septic tanks under subdivisions 74:53:01:23(1) to (3), inclusive, with the exception of outlet devices; and
(4) Holding tanks shall be installed to meet the requirements for septic tanks under § 74:53:01:24.
Source: 12 SDR 2, effective July 18, 1985; 13 SDR 129, 13 SDR 141, effective July 1, 1987; transferred from § 74:03:01:63, July 1, 1996.
General Authority: SDCL 34A-2-93.
Law Implemented: SDCL 34A-2-20.
Back to 74:53:01